Earlier in the week, areas in Tampines, Loyang, Bedok, Pasir Ris will have experienced voltage dips. It was made known later that it was due to a 22kV cable fault in Tampines area.
Few sets of our portable PQ analyzers placed in Loyang was able to capture this event. It registered voltage dips (at low voltage) of about 20%, lasting around 60-80ms. Recorded data showed that it was a three-phase fault.
One may be curious, how could a fault in Tampines result in a voltage dip in places like in Loyang or Bedok?
Our local distribution grid is densely interconnected, resulting in a high-reliability electricity network. Total blackouts are rare. But interconnectivity brings about a small disadvantage. Any fault will be seen/felt (in the form of a voltage dip) by everyone who is connected. The seriousness of this dip will be dependent on the types of faults and the electrical distance between you and the fault point.
Here in our case, the fault was in Tampines area. Based on experience, for a voltage dip ~ 20% to be seen at another 22kV network, it will need to be a significant fault causing a voltage dip in the range of 80-90% in the fault area (Tampines). Loyang (where our PQ analyzers were) is connected to Tampines at 66kV level.